Three Designs for PEX Plumbing Systemscomments (4) March 2nd, 2009 in Blogs
By Andy Engel
Incorporating manifolds into the layout can save water and energy because you eliminate most of the pipe between the water heater and the faucet. Although blue (cold water) lines are shown in these layout examples, hot-water layout would be similar. Three design options for PEX plumbing systems are: trunk-and-branch systems, home-run manifold systems, and sunbmanifold systems.
Trunk-and-branch systems are easy, but waste a lot of water
Traditional systems consist of large-diameter (usually 3/4 in.) trunk lines to distribute water throughout a house. Smaller branch lines (1/2 in. and 3/8 in.) tee off to feed individual fixtures. Trunk-and-branch systems have several disadvantages, notably a large number of fittings, which are costlier, slower to install, and more likely to leak than a single run of pipe. Also, a lot of water goes down the drain before hot water reaches the faucet.
Home-run manifold systems use the least hot water and the most pipe
A large-diameter (3/4 in.) main water line feeds the manifold; smaller lines run from the manifold to each fixture. Any fixture in the house can be shut off at the manifold. And because home-run systems don't rely on a large pipe for distribution, you save both water and energy. Simply put, you don't have to leave the faucet running as long before hot water reaches the sink. This design flexibility has a cost, however. Because a dedicated line is going to each fixture, you use a lot of PEX and drill a lot of holes.
Submanifold systems can be designed to save hot water
There are many ways to design submanifold systems, which require far less pipe and drilling than a home-run system. Rather than one main manifold, each bathroom, laundry, and kitchen gets its own submanifold. The simplest system, pictured here, won't save any water over a trunk-and-branch system, but other submanifold systems can be configured as water and energy savers by incorporating a main manifold and a recirculating pump.
|Read the complete article...
PEX Pipe: Is Copper On the Way Out?
Cross-linked polyethylene tubing is cheaper to buy, is faster to install, and won't corrode or explode
by Andy Engel
posted in: Blogs, energy efficiency, plumbing