I hope you can help me. I have an existing 3-way light switch (with 1 light on the circuit) ganged with a 2-way. I want to remove the 2-way and add the 2 lights on that circuit to be switched from the existing 3-way. I don’t mind leaving a non-working 2-way switch in the wall or getting a blank plate to cover it.
What should I do with the white and black wires on the 2-way to get this to work?
Thanks in advance