I just want to double check the wiring in one of our bathroom junction boxes. The box is 34 ci. We have a toggle switch and a double switch w/timer in the box. There are 4 x 14-2-g and 1 x 14-3-g wires. By my calculation, this box should be adequate. I had replaced the original box with the current box that is slightly bigger. The reason I have concern is because the new double switch w/timer (Pass & Seymour DEFL44L) takes up a lot of volume, and the wires just seem more cramped than might be allowed. But, even if I give the switch a 3 instead of a 2 for standard switches, I’m still in the calculated rating. Am I correct?