Unvented Crawlspace: Code requires the walls of an unvented crawlspace to be insulated. In most cases, there is then no need to install any insulation between the floor joists above the crawlspace. Some code authorities require rigid foam to be protected by a layer of 1⁄2-in. drywall, but an exception is often made for Thermax, a brand of polyisocyanurate that has passed fire-safety tests.Dan Thornton
If you live in the eastern half of the United States and want a damp, moldy crawlspace, just make sure that it is vented to the exterior. Within a few short years, the fiberglass batts installed in the crawlspace ceiling will become so damp that they’ll hang down like stalactites. You’ll end up with a classic moldy crawlspace—one that represents a significant source of moisture for the house above.
During the summer months, warm outdoor air holds more moisture than cooler crawlspace air. When that humid outdoor air enters the crawlspace vents, it hits cool surfaces—concrete, water pipes, and air-conditioning ducts—and condensation forms and begins to drip. One remedy that is sometimes attempted is to add a fan to the space, but that just increases the occurrence of condensation. The more you ventilate, the wetter the crawlspace gets. Crawlspace vents also can cause problems during the winter by introducing frigid outdoor air into the space, which can cause pipes to freeze.
Properly designed unvented (sealed) crawlspaces stay drier than vented crawlspaces, the pipes within them are protected from wintertime freeze/thaw cycles, and they require less insulation than vented crawlspaces (since the area of the perimeter walls is less than the area of the crawlspace ceiling). They also bring any ducts running through the crawlspace into the conditioned envelope of the house—an improvement that usually results in energy savings.
New-construction crawlspaces may require temporary dehumidification to remove construction moisture. Once the home is dried in, it’s a good idea to install a dehumidifier in the crawlspace and run it for three or four months until the interior relative humidity stabilizes. Also, remember that any combustion appliance (for example, a water heater or furnace) in an unvented crawlspace should be a sealed-combustion unit.Most building codes permit the construction of unvented crawlspaces. In recent versions of the International Residential Code, requirements for unvented crawlspaces can be found in section R408.3. If an unvented crawlspace has a dirt floor, the code requires exposed earth to be covered with a continuous vapor retarder with taped seams: “The edges of the vapor retarder shall extend at least 6 inches up the stem wall and shall be attached and sealed to the stem wall.”
In addition to the requirement of a duct or floor grille connecting the crawlspace to the conditioned space above, the code lists two options for conditioning unvented crawlspaces.
Option 1 (below): Install a continuously operating exhaust fan in the crawlspace that blows through a hole in the rim joist or an exterior wall. Make sure that the fan isn’t too powerful (1 cfm for each 50 sq. ft. of crawlspace floor area), because the makeup air entering the crawlspace is conditioned air from the house.
Option 2 (above): Install a forced-air register to deliver supply air from the furnace or air handler to the crawlspace (again, 1 cfm for each 50 sq. ft.). Assuming the house has air-conditioning, this introduction of cool, dry air during the summer keeps the crawlspace dry.
Detailing an Unvented Crawlspace
If you want to build an unvented crawlspace, follow these recommendations.
• To help keep the crawlspace dry, make sure the exterior grade slopes away from the foundation.
• Remove all rocks and debris from the crawlspace floor, and rake the dirt smooth. In new construction, it’s best for the crawlspace floor to be higher than the exterior grade.
• If the crawlspace is subject to water entry, slope the floor to a sump equipped with a drain or a sump pump.
• Install a durable vapor barrier—for example, a 20-mil pool liner or Tu-Tuf poly—over the floor. Extend it up the crawlspace walls, leaving 3 in. uncovered at the top to create a termite-inspection strip.
• Attach the top of the vapor barrier to the wall with horizontal battens secured with masonry fasteners.
• Seal the seams of the vapor barrier with a compatible tape or mastic. Many builders use duct mastic embedded in fiberglass-mesh tape.
• Install a 2-in.- or 3-in.-thick concrete slab to protect the vapor barrier, or install a sacrificial layer of 6-mil poly on top of the permanent vapor barrier to protect it from damage during installation of mechanicals and insulation.
• If testing shows high radon levels, install a passive radon-collection system below the crawlspace floor.
• Insulate the interior of the walls and rim joists with rigid foam or spray polyurethane foam. Many builders use Thermax, a polyisocyanurate foam that in most jurisdictions does not require a thermal barrier or ignition barrier. (Alternatively, you can insulate the exterior of the walls.) If your crawlspace has stone-and-mortar walls, you must use closed-cell spray polyurethane foam. Install at least as much insulation as required by the 2012 IRC for basement walls: R-5 for climate zone 3, R-10 for climate zone 4 (except marine zone 4), and R-15 for marine zone 4 and climate zones 5, 6, 7, and 8.
• Install an exhaust fan or a forced-air register as required by code (see “Code requirements for unvented crawlspaces,” facing page). Be sure that the fan does not exceed airflow requirements for the size of the crawlspace, since exhaust fans always carry an energy penalty.