Wiring a Master Suite Addition
Adding circuits for a new bedroom and bath offers lessons in rough electrical work and integrating new and old wiring.
Synopsis: Wiring a master suite addition is a comprehensive electrical project that requires skills and knowlege relevant to new construction and remodeling. Using a small addition as a case study, a licensed electrician talks us throught this process, from evaluating the existing electrical system to choosing the most appropriate boxes to pulling cable. In this article you’ll find the National Electrical Code requirements for bedrooms and bathrooms, and you’ll learn to read and edit an electrical plan. You’ll also discover the benefits of using a subpanel to power locations far from the main panel and learn how to integrate the new and old wiring.
It’s amazing how electrical-code requirements have evolved for the wiring in bedrooms and bathrooms, the rooms that make a master suite. These safety requirements are intended to protect against electrical fire in the bedroom when we’re asleep and vulnerable, and against shock and electrocution in the bathroom where electricity and water can be a dangerous combination.
When I started working on this 350-sq.-ft. master-suite addition, I received an electrical plan that met minimum code requirements in most instances and exceeded them in others. After going over the plan and examining the existing electrical system, I explained to the homeowners how I would integrate the new and old wiring, meet all the code requirements, and add a few upgraded features that would improve the comfort and convenience of their new master suite.
Begin by examining the old wiring
With the electrical plan in hand, the first thing I did on this job was to examine the existing wiring to determine two things: its condition and its existing capacity. In any master-suite addition wired to meet National Electrical Code (NEC) requirements, chances are you’ll need to add at least two new circuits.…